Application for Web Thermometers:
using email messages when limit values are violated
Set up email messages for your Web Thermometer which are sent automatically. This allows the respective technician to be notified directly when for example the temperature in the server room exceed a preset value. Here’s how it’s done:
1. Configuration of your Web Thermometer
Start up your unit by connecting the sensor, power supply and network cable and assigning an IP address using WuTility or DHCP. Then open the browser.
2. Log in
Open device configuration in the web browser and log in as "Administrator".
3. Configure mail server
Use "Communication paths" in the menu to go to the "Mail" page.
Check "Configure mail sending" and enter the desired parameters for the email server.
4. Create a message
In the menu under "Alarms/Message" create a new message by entering a trigger condition.
Further down on the page select "Email message" and enter the desired recipient information and the texts for the subject line and mail text. In addition you can configure texts for a "Clear Message" which is sent as soon as the alarm condition again reaches the valid range.
No problem: We will be happy to provide you with a unit for 30 days at no charge. Order the Web Thermometer as a sample and we will ship it to you for testing on open account. If you return the unit within 30 days, we will mark the invoice as fully paid.
Our qualified team of engineers will be glad to assist you.
You can reach us by telephone at +49 202/2680-110 or by email at email@example.com.